WBS and BEAB approved.
Manufactured in the UK in a BS EN ISO 9002 registered factory.
7 and 10 litre.
White moulded thermoplastic.
1.0kW, 3.0kW @ 240V.
0.9kW, 2.8kW @ 230V.
Frost protection thermostat setting.
Thermostat setting lockable at 40C for hand washing.
Flame-retardant expanded polystyrene.
Capillary type, externally adjustable from 5°C to 90°C.
Polypropylene, tested to 0.5 bar (7psi).
Only Vented taps must be used with Streamline heaters.
Cable entry at rear or base of unit. Must be permanently connected
to the electrical supply through a double-pole linked isolating
switch with a minimum rating of 13A (3kW model) or 5A (1kW
Bracket, screws and plugs supplied for wall mounting. For
undersink use the basic unit is inverted after the heating
element has been rotated.
All installations should be fitted with a service valve to
Minimum inlet pressure should be 0.34 bar (5psi) at which
maximum flow is 5 litres/min.
A flow restrictor (available as an accessory) should be fitted
for inlet pressures above 0.69 bar (10psi) to limit flow to
Supply direct from rising main or cistern (minimum head 4m)
using 15mm o.d. pipe. Cistern supply is not possible for all
outlet types; consult Heatrae Sadia for further advice.