Do not install the actual HOUSESAFE unit itself in new or renovated buildings
until all work including floor coverings is completed and the building has been
fully cleaned. The baseplate and wiring can be installed at any appropriate time
during the building progress. |
Excessive dust and debris from the actual building
work can contaminate the sensing chamber, causing problems. This will also invalidate
Installation of the alarm unit should be left to the end, simply
click fixing into place and commissioning at same time.
| |Do not insulate test this
(i.e. when testing house wiring
with megger, ensure alarm is disconnected).
1. Select a suitable
location, complying with advice given, which is wired in the conventional loop
in/out manner as shown below. Ensure mains supply is disconnected at all times
Previous - Next