WATER TANK: Hot water storage and cold water feed tanks are both manufactured from copper sheath with brazed seams
CASING: Corrosion proofed steel, white enamel finish.
INSULATION: 25mm foiled urethane core slab fully fire retardant.
SAFETY FEATURES: Master resettable rod type thermostat set of 80°C
APPROVALS: CE endorsed.
LOCATION: Wall fixing using the integral wall mounting bracket and fixing point.
It is Important to ensure that the wall is sufficiently strong to carry the weight of the water when full
The unit should be installed a minimum of 1 metre above the highest draw-off point. Sufficient distance must be allowed at the top of the unit for access to the ball valve and at the bottom to allow the withdrawal of the heating element.
PLUMBING: Cold inlet 1/2" bsp Left/right hand connection.
Hot outlet 22mm compression fitting
Drain connection supplied and fitted.
Ball valve assembly is for mains pressure operation, brass body construction to BS1212-2.
Should be installed to comply with bylaw 30. Overflow 22mm left or right hand connection
ELECTRICAL CONNECTION: Must be wired to a 13 Amp double pole fused switch