High Level Fan Heater N707
This attractive 3 kW heater is designed to complement
any decor and provide heat to the precise location it
is required by means of the swivel wall brackets. Recommended
mounting height is 2-3 metres from floor level. The
heater is particularly suitable for use in shops, factories,
warehouses and restaurants. This heater is not intended
to be used in areas containing flammable and/or explosive
Three position selection
Soft oyster grey colour. RAL 7035.
P.T.C. safety overheat cutout.
Wall brackets for angle mounting.
IP20, Class 1
Heated air volume 180m3/hr
Noise level 50dbA
The manufacturers reserve
the right to alter the specification of any product
without prior notice.
Industrial High Level Wall
INSTALLATION AND OPERATING INSTRUCTIONS
PACKAGING - Unpack the heater and remove any
LOCATION - The heater is designed for wall
mounting and is normally positioned at a point so that the
discharge forms a warm air flow over the area to be heated.
DO NOT COVER THE HEATER as this can cause overheating, and
may damage the unit and COULD ALSO CAUSE A RISK OF FIRE.
The heater is intended to be used in areas which are free
from any excessive dust and should not be used in areas containing
flammable and or explosive material. Minimum distance from
the ceiling is 300mm.
POSlTIONlNG - The heater must not be located
below a fixed socket. For optimum performance, the heater
should be mounted at between 2 and 3 metres above finished
floor level. Ensure the heater has adequate air flow around,
at all times, and no object is closer than 1.5 metres from
the discharge outlet.
WALL MOUNTING - The heater must only be mounted
horizontally. Fix the two mounting brackets to the wall 408mm
apart from screw fixing centre, with the coated finish facing
outwards. Select a set of mouldings comprising of a domed
shape, the grooved shape and two screws. Insert the grooved
shape with two clips facing towards the heater repeat the
process with the other side, now place the heater and align
the two 25mm holes with the mouldings and snap into place,
using the screws provided, screw the domed into place do not
fully tighten at this stage. Now the heater can be swivelled
in the desired direction and the screws tightened to lock
the heater in position.
CONNECTIONS - The heater is supplied with a
convenient length of suitable flex. Connection to the mains
should be made by way of a suitable switch, plug or other
device and in accordance with current regulations and protected
by an appropriate fuse or circuit breaker. Connect the heater
using the live cable, usually brown to the terminal marked
L, connect the Neutral cable usually blue to the terminal
marked N, and connect the earth cable usually green/yellow
to the terminal marked E, and having the symbol . THIS UNIT MUST BE EARTHED.
CONTROLS - Heater control is achieved by means
of a three position switch. The central position marked O
is off. Position marked I is fan only no heat, position marked
II is full 3kW heat output.
GENERAL MAINTENANCE ON ELECTRIC HEATERS
Prior to commencing any periodic cleaning or servicing always
ensure the supply to the heater is completely isolated. Bush
Nelson Electric heaters are factory assembled and tested they
are non user serviceable.
The heaters are intended to operate for many years, problem
All moving parts are factory lubricated and therefore should
require no service.
Maintenance is limited to keeping both the inlet and outlet
areas free from any accumulation of dust or any other foreign
materials. This is especially important immediately before
the heating season. Any dust build up can be loosened using
a brush and a vacuum cleaner applied to the airways to ensure
completed removal of any dust. When the heater is first turned
on after cleaning an unusual odour may be noted this is due
to the dust particles which inevitably will be disturbed and
will be burnt off from the heating element.
If in any doubt always consult a qualified electrician for
WARRANTY. Your Bush Nelson Heater is guaranteed for
the period of one year from the date of purchase. We will
repair or replace at our discretion any part found to be defective.
Bush Nelson cannot assume any consequential liability. This
guarantee in no way prejudices your rights under common law
and is offered as an addition to consumer liability rights.