|MCB Protection Rating
|Pump Motor Rating
|Click the image
for a larger version in a new window
Site Requirements - Water
To ensure correct operation, the pump must be connected to
a cistern fed supply of cold water. The pump MUST NEVER be
connected to the mains fed water supply. The cold water cistern
must always be above the pump to ensure priming of the unit
and at least 500mm above the sprayhead.
If used with a combination cylinder the cold cistern must
have a capacity of at least 114 litres to avoid starvation
of water to the pump.
Cold water supplies to the pump must be dedicated and separate
from any other supplies.
T450i has two flexible connections with 15mm push-in fittings.
Site Requirements - Electrical
The wiring must be connected to the switch without the use
of a plug or socket outlet. The supply cable selected for
installation must conform to the relevant table in the current
I.E.E. regulations. The minimum size will be 1mm2.
To enhance` electrical safety a 30mA RCD (Residual Current
Device) should be installed in all UK electric and pumped
shower circuits. This may be part of the consumer unit or
a separate unit.
Triton is registered by The British Standards Institute and
all Triton products are designed, tested and manufactured
under Quality Management Systems certified to BS EN ISO 9001
: 1994 and Environmental Management Systems approved to ISO
The Triton range of mains fed electric showers are covered
by a 2 year guarantee from the date of purchase (for domestic
use only). The T80si Pumped, T90si, and T450i are covered
by a 12 month guarantee. For a small premium this can be extended
to 3 to 5 years (for full details please see the warranty
application form included in every Triton shower pack).
Full fitting instructions are included in every pack. If
they would help you when planning your installation, a copy
is available on request from the Customer Service Department.
Installation should be carried out by competent tradesmen
in accordance with the detailed fitting instructions supplied
with every unit and in accordance with water regulations.
Trade Installer Hotline
Trade installers can phone a dedicated hotline on 024
76325491 for immediate technical advice on installation
and product suitability for commercial and multiple installations.